|Place of Origin:||XIAN, CHINA|
|Minimum Order Quantity:||1 UNIT|
|Packaging Details:||Solid Wood Packing wiht pallet|
|Delivery Time:||10 days after payment|
|Rated Voltage:||12kv||Main Circuit Rating Current::||160A, 250A, 400A, 630A|
|Number Of Pole::||3||Phase::||3|
vacuum contactor unit,
electrical vcb circuit breaker
Insulated Indoor Vacuum Circuit Breaker VCE Vacuum Contactor High Load Current
12kv High Voltage Vacuum Contactor
VCE VACUUM CONTACTOR AND VFC VACUUM CONTACTOR - FUSE COMBINATIONS
Product handling and installation should be handled with great care, so as not to damage the epoxy resin casting parts.
When Product lifting from the packing ,The wire should be hung in obvious signs of lifting hole, Moving can not make the
upper and lower arm force, At the same time, we should not let the product surface suffered serious impact .
Products have been strictly inspected before they go out, Parameters and functions conform to technical requirements
and rules. For the purpose of reliable, a first circuit must be carried out the following operations before charaging.
1 The installation box list be checked whether random file is complete ,and check whether the product nameplate and
certificate are consistent with purchase order .
2 Checking the product whether it have damaged, or other direct trauma .
3 Cleaning the products of insulation surface, transport pollution may affect the product in the process of insulation
4 Using the method of secondary electrifying to test the opening and closing operation of the switch, Observing
whether the state of the switch position indicator is normal .
5. VFC handcart should be pushed by service handcart rack, and wave in the test, the product in the opening condition
should be able to smooth move between the working position and test position.
Products should be tested before formal operation of power frequency withstand voltage test, we consider the power
frequency withstand voltage test for many times under the influence of the unrecoverable isulating performance, and do not
recommend according to the full capacity to test, 10 kV products shall be carried out in accordance with the 38 kV 1 min, 7.2
kV products shall be carried out in accordance with the 28 kV/ 1 min.
The installation of VFC basic operation can refer to the middle-placed handcart installation of circuit breaker .
Applying ambient conditions and matched switch panel width
Contact Person: Dong